|Place of Origin:||China (Mainland)|
|Model Number:||Coal Fired Steam Boiler|
|Minimum Order Quantity:||1 set|
|Packaging Details:||wood packet|
|Delivery Time:||15 days|
|Supply Ability:||5 SETS per month|
|Steam Capacity:||1-10t||Working Pressure:||1.25/1.6MPa|
|Steam Temperature:||193/204℃||Feed Water Temperature:||20℃|
|Boiler Efficiency:||82%||Water Volumn:||4.5-16.5m³|
coal burning boiler,
hard coal boiler
1. Easy installation:
Boilers are generally installed out of the factory quickly, which is convenient for transportation and site installation, greatly shortens the construction cycle, saves installation costs, and enables the boiler to be put into production in time.
2. Reliable operation:
Boiler heating surface layout is reasonable, water circulation is smooth, ensure that the heating surface cooling in time, thus effectively ensuring the safe operation of the boiler.
3. Maintenance and maintenance are convenient:
The boiler drum is equipped with manholes, which can be inspected and repaired. The smoke box in front of the boiler is easy to open, and the personnel can check it conveniently and clearly, which provides a good condition for the correct treatment.
4. Full combustion:
With secondary air and reasonable furnace design, the fuel can be fully burned and the black smoke can be eliminated.
5. High efficiency grate:
Boiler grate is matched with biomass fuel, which avoids air leakage, fuel leakage and uneven ventilation. It is easy to operate and has obvious advantages compared with ordinary grate.
6. Cleaning is convenient:
The installation of multiple ash clearing holes on the boiler can effectively clear the ash in time, avoid the operation obstacles and the decrease of thermal efficiency caused by the ash accumulation of the boiler, and ensure the stability of the boiler load.
Main Technical Parameters of DZH Series Biomass Steam Boiler
|Feed Water Temperature||℃||20||20||20||20||20||20||60|
Note: The fuel consumption in the table is calculated on the basis of the low calorific value of biomass particles 17084KJ/Kg (4085Kcal/Kg). If the low calorific value of biomass fuel is larger than that, the corresponding fuel consumption will be more economical than that in the table.
Shape and Interface Dimensions of DZH Series Hand-fired Biomass Steam Boilers
|Rated Steam Capacity||t/h||1||2||3||4||6||8||10|
Host Transport Dimension
|Host Transport Weight||/||t||13.6||18||23||25.3||31||34||39|
|Main Steam Valve Pipe Diameter||DN||mm||65||80||100||100||125||150||150|
|Feed Water Valve||DN||mm||40||40||40||40||50||50||50|
|Safety Valve Diameter||DN||mm||2×40||2×50||2×50||2×50||50/80||2×80||2×80|
|Drain Valve Pipe Diameter||DN||mm||3×40||3×40||3×40||3×40||3×40||3×40||3×40|
Remarks: We will reserve rights to change the above mentioned data due to continuous policy transformation and product improvement.
Contact Person: Xu